This particular service drop and entry was suspect on initial inspection. The lowest point of the service conductor, the drip loop, is less than 9 feet from grade. This can be determined by counting the bricks. The width of each brick is 2 ¼ inches adding a mortar joint brings it to about 3 inches. This method is better than using a metal tape measure to check the height and a lot safer! There are 33 rows from grade to the bottom of the drip loop. 33 x 3 = 99 ÷ 12 = 8.25.
This would then mean the service drop is also too low. The margin of his rough estimate (over one foot) is certainly wide enough to warrant further evaluation by an electrician. The service entry conductors' height will likely need to be extended to fall within the safety parameters previously discussed.
Taking risks with electricity is never advisable. Minimum safety requirements are in place to protect people from serious injury or death. A knowledgeable home inspector can heighten your awareness of potential problems and spare you shocking surprises after your purchase.
JRV Home Inspection Services, LLC